The combination of power receptacles, ground jacks and the ground bus within a single enclosure offers convenience and substantial labor savings in field wiring over individual receptacles and ground jacks scattered on the operating room walls.
The Power & Ground Module unit includes Hospital Grade power receptacles, Ground Jacks and a ground bus with ample lugs for external ground connections.
The power receptacles are Hospital Grade and may be any of the following:
The number of receptacles may vary from 1 to 4 and in special cases more.
The ground jacks are extra heavy duty as described in NFPA Standard 99.
The ground bus consists of forged copper with 24 taps for #14-6 and a main lug of 250MCM-#6 wire ranges.
The power receptacles and the ground jacks are mounted on the 304 stainless steel, brushed finish trim. To insure uniform finish and the minimum of screw heads, special screw studs for mounting the receptacles are welded prior to application of the #4 brushed finish. The ground bus is mounted to the rear of the code gauge steel, baked enamel backbox. This allows all external ground wires to remain undisturbed if the front must be removed for servicing.
|4 Ground Jacks + 2 Red Duplex Receptacles||358051|
|4 Ground Jacks + 4 Red Simplex Receptacles||358250|
|4 Ground Jacks + 4 Twist Lock Receptacles||358351|
|2 Ground Jacks + 2 Red Duplex Receptacles||358432|
|4 Ground Jacks + 4 Red Duplex Receptacles||358574|