The Low Profile Low Voltage Controller enables users to safely operate the high-voltage lighting found in hospitals and other medical facilities. Appropriate for applications using fluorescent, LED and other lamp types, they are tested and approved with all Nurse Call systems that use a switch. Controls two loads independently, or two loads sequentially and is safe to use near medical equipment that is sensitive to electromagnetic noise.
Designed to mount inside a lighting fixture all connections should be made within the lighting fixture and capped.
The wires on the low voltage side of the units are designated as red, blue and brown. When wiring as a single momentary switch, sequential controller, you must connect the red and blue wires together to one side of the switch. The brown wire is the other side of the switch. Wiring can be connected to a receptacle or directly to a pillow speaker if it is hard wired to the curse call system. When wiring as a two switch combination control, the brown wire is common for the two switches, Blue is S1 and red is S2 (see diagram on page 2)
On the high voltage side the wires are grouped as AC voltage, AC voltage out to the load (light) and input voltage designation.
277VAC, 5A, General and Ballast Use
|5VDC @ .5 mA
|.032” Galvanized Zinc-Plated steel
Part Number 028618